Apr 26, 2022
Sam Myers with Retrotec talks to Bryan about pressures in the home and why they matter for HVAC solutions at IBS 2022.
Technicians focus a lot on ductwork and airflow, but many of them don’t focus on how the building envelope impacts HVAC performance. A lot of the HVAC equipment’s performance is affected by the push and pull of air caused by leaky areas in the building envelope.
If you have a room with too much air and another room with too little, you will have unbalanced pressures. Unbalanced pressures may result in discomfort and latent load issues, especially when unconditioned air is pulled in through the attic. Sealing the envelope well and using dampers as necessary can minimize the comfort issues caused by pressure imbalances in the home.
Instead of just using manometers for static and gas pressure, we can also use high-resolution manometers under doors to pick up pressure differences. However, the manometer MUST be high-res to pick up those subtle (but palpable) differences in pressure. A blower door is also a great tool, especially when you use it with a thermal imaging camera; the blower door amplifies the temperature effects that a thermal camera will detect, especially if you also have a good delta T.
If you have an iPhone, subscribe to the podcast HERE, and if you have an Android phone, subscribe HERE.
Check out our handy calculators HERE.